Available in sizes 14 AWG through 750 KCMIL, Encore Metal Clad Cable is constructed with soft-drawn copper, Type THHN/THWN-2 conductors rated 90 C dry locations, Larger sizes are supplied with a bare ground conductor.
Sizes 14 AWG through 1 AWG contain a green insulated grounding conductor.
All conductors are cabled together with separator tape containing the identification print legend to form the cable core.
Interlocked aluminum armor is applied over the entire assembly.
Permitted use for services, feeders, and branch circuits in industrial, commercial, and multi-residential buildings.
Permitted use in dry locations and embedded in plaster finish on brick or other masonry except in damp or wet locations, Allowable installations in approved raceways and cable trays (NEC 392).
Utilized for environmental air-handling spaces (NEC 300.22)(C). Allowable in assembly occupancies (NEC 518.4).
Permissible in theatres, audience areas of motion pictures, television studios, and similar locations (NEC 520.5).
Permitted in Class I Div. 2, Class II Div.2, and Class III Div. 1 Hazardous Locations and listed for use in UL 1, 2, and 3 Hour Through-Penetration Firestop Systems,
Suitable for installation under raised floors for IT equipment (NEC 645.5). Acceptable for power, lighting, control, and signal circuits. Allowable in concealed or exposed systems.